Fifty + years conditioning the air.
Answer questions about , residential and commercial. Answer questions about sheet metal fabrication. Fifty years plus experience. No answers for oil equipment, No answers for kitchen appliances, No answers for laundry appliances, I don't specialize in one particular area of the HVAC area, I'm more of a General Practitioner, Limited in refrigeration/
Hands on since 1950
|James||06/06/16||10||10||10||Jim, it ended up being a loose .....|
Richard, A refrigerated air conditioner unit when turned on, first it takes the humidity out of the air before it starts to cool, when the room air goes in the coil condensates and the water drips out
Richard If your talking about a refrigerated AC unit, They all have to drain water.
al, The outside condenser motor has a thermo disconnect switch built in, if the motor over heats it turns off, when the motor cools the switch re-connects and runs again until it over heats again, The
Carl, It is a 2 ton unit. one ton of cooling for 400 sq feet of space. Give or take depending on heat or cooling loss. Top floors have more exposure to the elements, When measuring sq footage
Carl, The larger return air grils are 30x6, the smaller ones are 14x6 . The grills have 50% free air capacity. The openings down through the floor are even smaller. Yuo may only have a total of 210
Answers by Expert: