40+ years diversified experience.An HVAC/Refrigeration Self Employed Contractor since 1986. NATE Certifield. Answer questions pertaining to Residential and Commercial Air Conditioning , Warm Air Heating, Heat Pump systems.Mechanical and Electrical troubleshooting of these systems.Be as detailed as possible when describing problem.Packaged unit or split systems.No appliance questions.
Installation and Troubleshooting, Mechanical and Electrical, in following areas, Refrigeration ( Walk In and Reach In Coolers and Freezers ) Commercial Roof Top and Packaged Heating/Cooling ( Natural Gas,Propane, Electric, and Heat Pumps ) Computer Room Air Conditoning Systems,Commercial Residential Packaged and Split Systems Air Conditoning and Heat Pumps.Warm Air Oil , Natural and Propane Gas Heating systems.
Graduated from Private Technical School in 1975. An HVAC/Refrigeration Contractor . Have Unlimited Heating/Piping and Cooling Contractor License.Limited Sheetmetal Contractors License.NATE Certifield. York Certifield Master Heat Pump Technician 1986. Served 33 years combination Active Duty Air Force , Air Force Reserves and Air National Guard in the HVAC/Refrigeration Shop/Mechanical Shop. Troubleshooting/Installing HVAC/Refrigeration Equiptment Worldwide. Retiring in 2003 as a Senior NCO ,and a Mechanical Superintendent.
What fan is kicking on ( if this is a split system two piece unit ) the indoor fan or outdoor fan. If it's the indoor and the OD unit is not kicking on, possible the breaker for the OD unit tripped or
Doug, To me furnace humidifier work when calling for heat only, so if you have a relatively short run times I don't think your humidifier will add much %. I would lean more toward a portable humidifier
Mark, I would remove the face grille to see how much quieter your return noise is. If it's relatively quiet you can bend the louvers upwards for less restrictions using a needle nose plier. You can
Mark, That would depend on what size wire you have , 14 gauge is good for 15 Amps. I believe. You may want to ask a electrician at this site. You should look at the data plate on your heater for the
John, The first thing your really suppose to do is a load calculation to determine exactly what size system you need, as your one ton off between the two contractors. How did the first Contractor calculate
Answers by Expert: