I can't help you if your whatsis won't work, people (Especially if it's a refrigerator); I have no experience with appliances, and I haven't been involved with H&AC service and repair since March 08, 1996 (Thank the Lord); I always send a "standard" reply to appliance questions and H&AC "Service and Repair" questions (about 20 a month), so if you want to know why your whatsis isn't working like it used to, ask someone else. A lot of my answers arenít read by the questioners; in that event, I always send reminders to read the answers for a month or more (the word "idiots" comes to mind - actually there's another more appropriate word, but discretion prevents its use here). If you have questions about how big a unit you need, if one room's warmer than the others, if you want an opinion oas to scope of work on bids received, etc. just ask. Do visit www.askweldin.com, there's a lot of good information on sizing, ductwork, efficiency, as well as some techniques accomplished DIY-ers can use to troubleshoot and improve their H&AC. Finally, I want to thank all of the kind, serious people whom I meet here: I enjoy working with you. My wife says I'm "snarky" from time to time; as for you others, please use your imagination as to the responses swirling on the snarky side of my brain when I read your questions.
53 years in the business. See www.askweldin.com
B of ME U of D 1965, numerous classes, seminars and a lot of "Hands On" learning since.
Helping homeowners who've gotten a raw deal. Really.
I would love to be put out of work because the industry cleans up its act.
Contractors frequently (deliberately?) misdiagnose ductwork problems as insufficient cooling: Some rooms are not cooling, so the system must be too small; it's good business for a contractor. In fact, I've never seen an undersized residential system; the most frequent problem is "Too Much Equipment, Too Little Ductwork". I normally reduce cooling capacity when I develop an Improvement Plan.
Installing ductwork is a labor intensive operation, and many contractors profit by doing it too quickly. The end result is energy intensive: Conditioned air leaks to/from unconditioned spaces, too much heat is gained/lost because of improper insulation, rooms are overheated/overcooled because the system can't be balanced, etc.
Howard: You omitted the "6" from the AC M/N (SHB "NXA6..."). The HXA6 is a heat pump. They're both 16 SEER. I presume you're replacing outdoor unit, indoor coil and air mover (furnace???), because
Micheal: Any duct 18" or wider must have the pins. Note that I prefer weld pins to adhesive pins, which cal detach. The average installed thickness must be at least 2-1/4" to achieve R( "Installed Value"
There are no ratings for that unit at AHRI. I did run across a Ruud UPMC service manual indicating it's a 12 SEER. However, the coil is not a Ruud product, so the rating of your combo is unknown. Again
Hello Adriane! You'll need more info: I think you've provided the M/N of the cooling coil, but you'd need the mfgr. and M/N of the associated outdoor unit and furnace M/N (Lendell appears to be a furnace
Return grille: 20x20 H&C #672 (in a plenum base w/ unit in upflow configuration?). Supply main: 16x8, reducing to 12x8 after four registers. Route the main along the center of the 38' dimension. Do
Answers by Expert: